These Technical Questions and Responses have been collected by ABSA Design Survey and have value to prospective submitters for clarification on processes, general policies, and some specific scenarios for design submissions. Followings are related to general registration requirements.
1.R1. Section 2(2)(n) of the Pressure Equipment Exemption Order (PEEO) exempts pressure equipment, other than boilers, with a volume not exceeding 42.5 L that is the subject of a research experiment in a research facility, or, that is part of a temporary apparatus being used in a research experiment in a research facility from the PEEO. Equipment that is exempt from the PEEO does not require design registration
2.R1. The definition of pressure in section 1(1)(z) of the PESR means a positive gauge pressure, i.e. any pressure above the local ambient atmospheric pressure. It is not a pressure above one atmosphere (approx. 14.7 psi) gauge pressure.
3.R1. The Forewords to the various sections of the ASME Boiler and Pressure Vessel Code state the following:
This means that one should be in the habit of ordering material to the appropriate ASME SA or SB specification number. However, if the material provided is only documented as meeting an ASTM A or B specification number of a specified edition date and that specification number and date are included in the Guidelines for Acceptable Editions in Section II, Part A or B, the material is acceptable for Code construction within the limitations of the Code of construction. See the second last paragraph of the Foreword to any Section of the Code for additional detail. The above comments apply equally to non-ASTM material specifications that have been incorporated into Section II under SA or SB specification numbers.
4.R1. Not all repair procedures must be registered through Design Survey. Per section 40(3) of the PESR, “repairs … shall not be undertaken without the prior agreement of a safety codes officer.” If the safety codes officer is of the opinion that the repair procedure is complex enough to require the involvement of Design Survey, he or she will require the repair organization or the owner of the equipment to be repaired, as appropriate, to submit the procedure to Design Survey for registration.
Note: The above applies only to repair procedures; all alteration procedures must be registered through Design Survey.
5.R1. No, although ISO 16528 is now under PESR section 6(k), it is not an alterative design code/standard, i.e. we are not accepting that in lieu of the listed adopted codes and standards under Section 6(a) to 6(j). As per Information Bulletin No. IB11-013, the applicable listed adopted code(s)/standard(s) under Section 6(a) to 6(j) must be used for the construction of boilers and pressure vessels (and components forming parts thereof). The intent of the addition of Section 6(k) is only for things that are not addressed by any of the codes and standards adopted under Section 6(a) to 6(j), then a code or standard in conformance with ISO 16528 may be used in accordance with the new Section 6(k) of the PESR provided that “the same engineering philosophy, safety margins and administrative requirements in the CSA B51″ must be followed.
6.R1. A CRN for a boiler or pressure vessel is defined by CSA B51 Clause 4.3 as:
- consisting of a letter, four digits, and a decimal point followed by up to ten digits and three letters
the first letter and four digits are part of a sequential numbering system used by the issuing province or territory
- the first digit or letter to the right of the decimal point indicates the province that issued the particular number
- the following identifications are used in accordance with the code:
1 – British Columbia 7 – New Brunswick 2 – Alberta 8 – Nova Scotia 3 – Saskatchewan 9 – Prince Edward Island 4 – Manitoba 0 (zero) – Newfoundland 5 – Ontario T – Northwest Territories 6 – Quebec Y – Yukon Territory N – Nunavut
- the letter C may follow the designation of first registration if a design is registered in all jurisdictions. No jurisdiction issues the letter C; it is a convenience for stamping once the manufacturer has received all the registrations.
- the letters CL may follow the designation of first registration if a design is registered in all jurisdictions that require registration and is not registered in the jurisdictions that do not require registration. No jurisdiction issues the letter CL; it is a convenience for stamping once the manufacturer has received registrations for all jurisdictions that require registration. (The “L” means limited.)
- to be eligible for use in Alberta, the CRN must have the digit 2, or the letter C, somewhere after the decimal point.
- A Canadian Registration Number or Pressure Piping number is issued if the design is satisfactory.
For example, the following could be valid CRNs: B1079.23, M2138.5C and V1234.5CL.
7.R1. Please see article – What are the Major Differences Between ASME VIII Divisions 1, 2 and 3?
8.R1. No, ABSA does not have the authority to enter into an agreement with any person or company that would restrict government’s regulated access to and use of the records collected because ABSA is a Delegated Administrative Organization under the Safety Codes Act of Alberta, not a private corporation. Our authority and scope of our activities are granted by the Province of Alberta and governed by the Alberta Safety Codes Act and The Government Organization Act – Boilers Delegated Administration Regulation (AR32/2002). ABSA records must comply with section 7 of the Boilers Delegated Administration Regulation, which also references the Records Management Regulation (AR224/2001). Links to these Acts and regulations are available via The Queen’s Printer, or accessed through our website Act and regulations
For related information see Design Drawings of Record Management
For additional information please contact Alberta Municipal Affairs. Alberta Municipal Affairs is the government department to whom ABSA reports. They can be contacted toll free at 1-866-421-6929. This number is for the Safety Services Branch of the department.